Overview: This industrial brackish RO equipment was constructed to treat well water and reduce the TDS for general use in a mall in Kuwait.
Industry: General Use
Water Concern: Public facilities like malls or entertainment centers require water for general human use. These applications range from drinking fountains to toilet water. Therefore, a systemic water filtration system would best suit the requirements for all the applications. Supplying water from a well source usually includes an abundance of elevated parameters. The concern for this customer was reducing the TDS levels to accommodate the intended applications of the facility. This customer had a well water supply that contained 8,000 PPM TDS and was looking to produce 600,000 GPD.
Applied Solution: This industrial brackish RO equipment was recommended and constructed for a public mall facility in Kuwait. The capacity of this RO equipment was 600,000 GPD and the product is intended to be the main supply of water for the facility. This system includes the necessary pre-treatment and post-treatment units that keep the RO equipment functioning efficiently without any problems. Part of this pre-treatment is duplex multimedia filter to reduce turbidity and suspended solids. The pre-treated water continues on to a 5-micron cartridge filter to further reduce any leftover suspended solids and is injected with sodium metabisulfite along with antiscalant for chlorine reduction prior to reaching the RO membranes. Then, the water is pressurized by high-pressure pumps through the RO membranes that will raise the pressure to 300 PSI. The water exiting the system results in a product and reject stream.
This equipment included a RO model #BW-600K-13780-8 from our RO-500 Series in addition to a Multi-Media Filter model #MLF-72 from our MF-1000 Series.
·(13) FRP pressure vessels Protec rated at 300 PSI model PRO-8-300-MSP-7
·(91) 8" TFC spiral wound membranes Hydranautics ESPA2-LD
·ORP on feed line and pH on product line
·Low- & high-pressure switches
·Paddlewheel flow meters
·Two high pressure pumps CRN90 with 2 VFDs
·Two 5-micron pre-filter with SS housing (SSC-88-316)
·Siemens S7-1200 PLC controller with HMI screen
A brackish RO equipment was fabricated to produce water for general human use for a mall in Kuwait.
This is a Reverse Osmosis (RO) Plant that was contracted for a mall in Kuwait. The capacity of this RO Plant is 600,000 GPD. The application for this will be as the central water filtration system for the mall. This RO Plant contains all the pre-treatment and post-treatment that keeps the RO Plant functioning efficiently without any problems. The pre-treated water is passed through the Media Filters with a 5 micron membrane, then to the High Pressure Pumps that will raise the pressure of the water to 220 PSI. From there the treated water is sent to either the Product Line or the Reject Line. For more info: https://www.pureaqua.com/industrial-brackish-water-reverse-osmosis-bwro-systems/
Join our subscribers for more videos