Application: Apartment Buildings
Water Challenges: The challenge of hard water is a recurring one throughout apartment buildings that face the deterioration of their equipment as a result of the water’s effects. Hard water contains minerals such as magnesium and calcium, which are prone to scaling on equipment and appliances used in apartment buildings. This harms the productivity of the apartment building since these equipment are no longer able to operate efficiently and require greater maintenance or even replacements as they continue losing performance capabilities.
Applied Solution: Pure Aqua manufactured and supplied automatic water softeners to a major company in the USA for export to Saudi Arabia.
The water softener unit was created and executed in order to remove hardness from water. Hardness in water does not allow soaps to work to their full capacity. Hardness makes it difficult for clothes to be cleaned and leaves skin with a "slippery" feeling. The way the twin alternating softener unit works is by having one tank remove hardness while the other is regenerating. The first tank is full of resin that is saturated in sodium ions. As water is going through the cycle, the resin attracts the calcium and magnesium ions that make the water hard. This then leaves the water with only sodium ions which do not have the same effect on soaps and detergents as calcium and magnesium ions have which leaves the water "soft". Once the first tank is full to capacity of taking calcium and magnesium ions, the tanks switch roles. Now the second tank will accept the role of removing hardness from water. The regeneration part of the process flushes a solution full of sodium ions through the tank, the resin now releases the calcium and magnesium ions and absorbs the sodium ions. This leaves the tank and resin in its original state again in order to repeat the process. The calcium and magnesium ions are discarded leaving the water soft and ideal for usage in hotels, schools, or restaurants.
This is model 29F24300T from our SF-250A Series.
- Twin Alternating Water Softener
- Two 24” Diameter Stainless Steel Tanks
- Fleck Multiport Valves
- Produce 97,920 GPD
- Power & Energy
- Well Water
- Environmental Water Treatment
- Refinery Water Treatment
Pure Aqua Inc. fabricated a commercial twin alternating water softener unit for a major company in Saudi Arabia. The unit included two 24" diameter stainless steel tanks and controlled by Fleck multiport valves. The system was designed to produce 97,920 GPD. Click here for more information: http://www.pureaqua.com/commercial-water-softener/
Join our subscribers for more videos